[TRNSYS-users] about control strategy a pump
emrearpaci10 at gmail.com
Fri Dec 6 12:45:27 PST 2019
Jeff you are awesome
Jeff Thornton via TRNSYS-users <trnsys-users at lists.onebuilding.org>, 6 Ara
2019 Cum, 23:28 tarihinde şunu yazdı:
> You'll need to use a forcing function and set the non-summer months to a
> value of 1 and the summer months to a value of 0. Then simply use an
> equation and multiply the control signals together:
> On_Off_Pump = NotSummer * Type2ControlSignal
> where NotSummer is an equation connected to the Type 14 forcing function
> and Type2ControlSignal is an equation connected to the output of the Type 2
> differential controller. Then simply connect the On_Off_Pump equation to
> the input control signal for the pump.
> Jeff Thornton
> President - TESS LLC
> 3 N. Pinckney Street, Suite 202, Madison WI USA 53703
> Office: (608) 274-2577 Fax: (608) 278-1475www.tess-inc.com
> E-Mail: thornton at tess-inc.com
> On 12/06/2019 1:41 pm, Emre Arpaci via TRNSYS-users wrote:
> hi trnsys user
> good weekend wishes
> I m controlling a pump with type 2b. I want to do that my pump would
> control with type 2b but in summer season (june ,july august) the pump
> would always off.
> Can I do this with trnsys and how ?
> I shortly mean
> 9 months contro with differential element type 2
> summer season is off.
> TRNSYS-users mailing listTRNSYS-users at lists.onebuilding.orghttp://lists.onebuilding.org/listinfo.cgi/trnsys-users-onebuilding.org
> TRNSYS-users mailing list
> TRNSYS-users at lists.onebuilding.org
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the TRNSYS-users