karaktus at gmail.com
Mon Jun 24 05:42:47 PDT 2019
I used an equation outside type56 with occupancy and season as an input
to the equation*.
Le 24/06/2019 à 13:40, Sam Elyas a écrit :
> Hi Aya,
> I had to deal with the same issue recently, I used an input and set
> the setpoints in order to not have cooling when there is no occupancy.
> to achieve that I "26*Occypancy*SeasonC+100*(1-Occupancy*SeasonC)"
> where seasonC is the cooling season, Occupancy is an input from type14
> (and 41a) schedule.
> Hope that helps.
> Le 24/06/2019 à 09:20, aya khalil via TRNSYS-users a écrit :
>> Dear ,
>> /I trying to calculate the cooling demand of my office // building in
>> TRNBUILD and would like the cooling demand to //response according to
>> my occupancy schedule(less cooling at //night and more cooling at
>> day). I try to define the set temp // at the cooling type by i not
>> sure which one should i use /(/schedule or input?) And also the
>> equation behind it,// because when i enter like for instance
>> _25degree(set temp) //*occupancy schedule+0_, i would get 0 degree
>> when there is // no occupancy. // Appreciate your kind assistance on
>> this Email /
>> /Aya khalil /
>> /Master student at usj-beirut /
>> TRNSYS-users mailing list
>> TRNSYS-users at lists.onebuilding.org
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the TRNSYS-users