[Equest-users] eQuest Floor Multiplier vs System Multiplier
Daric.Adair at hendersonengineers.com
Tue Aug 27 12:47:03 PDT 2019
Am running into some confusion on the use of multipliers; and how the do/don't appear to cascade out to HVAC Systems. If I create a 10 story building in the DD Wizard with 'use multipliers' checked and 'HVAC System per Level', this creates a building with the area of the 10 story building, on 3 floors, with 3 HVAC systems. Granted the middle floor has a floor multiplier of 8, which is linked to the spaces and zones - but not the systems. Thus, it is really 3 AHU's - top, bottom, and a much larger AHU for the middle floor(s).
I have been unable to find anything in the documentation that say 'oh, by the way, this is floor multipliers don't multiple HVAC Systems' or 'Don't use this if you really do have multiple HVAC system." Which is both odd, but unsurprising all at the same time.
This approach could impact model performance, especially if performance curves do not scale in a multiplier fashion or if one is unaware of this behavior and looks up incorrect efficiencies based on the 'multiplied' unit's capacity. It also impacts reporting to LEED/Code if they see 3 systems (from my example) and not the 10 AHU's/RTU's scheduled.
Question is two part:
1. is this behavior correct with other's experience?
2. There is no means within eQuest to specify a Systems multiplier?
I see where multipliers could be used, but that isn't my applciation here.
DARIC R ADAIR PE, CEM, BEMP
Mechanical Engineer, Energy Analyst
daric.adair at hendersonengineers.com<mailto:daric.adair at hendersonengineers.com>
Licensed in KS
Sending me large files? Please use Henderson File Share<https://apps.hendersonengineers.com/FileShare/Uploademail@example.com> | TX ID #F-001236
This email and any files transmitted with it are confidential and are intended solely for the use of the individual or entity to whom they are addressed. This communication represents the originator's personal views and opinions, which do not necessarily reflect those of Henderson Engineers, Inc. If you are not the original recipient or the person responsible for delivering the email to the intended recipient, be advised that you have received this email in error, and that any use, dissemination, forwarding, printing, or copying of this email is strictly prohibited. If you received this email in error, please immediately notify administrator at hendersonengineers.com.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users