[Equest-users] Not able to model 13 chillers under one circulation-loop chilled water loop
David Griffin II
DGriffin at archnexus.com
Wed Jun 13 13:24:11 PDT 2018
I have not run into this issue in the past. However, the error message suggests there is a limit to the number of chillers and/or other equipment that can be attached to any given circulation loop. That aside, I have an idea I wanted to share with you that may or may not fix your error issues.
Most loops are setup in an N+1 fashion; i.e. there is an extra piece of equipment installed on the loop incase a failure occurs. That way the process being served by the loop doesn’t lose it’s ability to serve it’s funciton when one of the chillers fails. If this is the case for your project, simply reduce the number of chillers on your loop to 10 (the maximum pieces of primary equipment per loop) and your model should run.
I hope this helps!
[ARCH | NEXUS]<http://www.archnexus.com>
DAVID W. GRIFFIN II
2505 E Parleys Way
Salt Lake City, UT 84109
From: Nitin Harjai [mailto:nitin.harjai28 at gmail.com]
Sent: Wednesday, June 13, 2018 10:00 AM
To: equest-users at lists.onebuilding.org
Subject: [Equest-users] Not able to model 13 chillers under one circulation-loop chilled water loop
I am facing problem when I try to model 13 chillers in water side HVAC and getting error while performing simulation.
I am getting error "For Circulation-Loop Chilled Water Loop. Maximum of ten attached primary equipment units was exceeded."
Can anybody tell me that is there any limitation issues considering the chiller quantity in equest.
Please help me.
Nitin J Harjai
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users