[Equest-users] Not able to model 13 chillers under one circulation-loop chilled water loop
Daric.Adair at hendersonengineers.com
Wed Jun 13 13:19:55 PDT 2018
Yes. I believe 10 is the limit. I have hit that before on a Hot Water Loop with Boilers before.
DARIC R ADAIR PE, CEM, BEMP
Mechanical Engineer, Energy Analyst
daric.adair at hendersonengineers.com<mailto:daric.adair at hendersonengineers.com>
Licensed in KS
From: Nitin Harjai <nitin.harjai28 at gmail.com>
Sent: Wednesday, June 13, 2018 11:00 AM
To: equest-users at lists.onebuilding.org
Subject: [Equest-users] Not able to model 13 chillers under one circulation-loop chilled water loop
I am facing problem when I try to model 13 chillers in water side HVAC and getting error while performing simulation.
I am getting error "For Circulation-Loop Chilled Water Loop. Maximum of ten attached primary equipment units was exceeded."
Can anybody tell me that is there any limitation issues considering the chiller quantity in equest.
Please help me.
Nitin J Harjai
This email and any files transmitted with it are confidential and are intended solely for the use of the individual or entity to whom they are addressed. This communication represents the originator's personal views and opinions, which do not necessarily reflect those of Henderson Engineers, Inc. If you are not the original recipient or the person responsible for delivering the email to the intended recipient, be advised that you have received this email in error, and that any use, dissemination, forwarding, printing, or copying of this email is strictly prohibited. If you received this email in error, please immediately notify administrator at hendersonengineers.com.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users